normal water flow for the ROWPU is related to the type of water and its
temperature as listed in Tables 1-2 and 1-3.
Higher water flows, up to
listed limits, may be set under "push" conditions to meet unusual mission
demands. Do not push beyond the flow listed for 75 degrees F when operating
on well water sources. Operating at push conditions may damage RO elements
and require more frequent cleaning.
Do not exceed 900 psig on system
Average Mission Water Flow for Fresh/Brackish
Water Sources (0-15,000 PPM TDS)
Average Mission Water Flow for Sea Water
Sources (Up To 37,000 PPM TDS)
Adjust the voltage to provide 435 to 445 VAC.
c. Check the high pressure pump assembly for noise and excessive
Noise and vibration can be diminished by slowly decreasing or
increasing the air pressure in the stable level air mounted bags.